Contractor shall provide power and install new pumps to existing condensate receivers located at Building 010 on the BARC West campus. Provide and install new sump pumps to two pits at the west end of building 010. Replace the two condensate pumps on the condensate receiver in building 010, room B204.
Contractor shall provide 3 phase power and single phase power from the existing emergency electrical generating panels located in the Greenhouse and distribute it to an existing electrical pedestal style breaker panel.
This panel is located outside building 010 at the south west corner. Connect 3 phase power to 2 (two) existing condensate receivers located at the vault located outside building 010 near the double doors (Vault #1), Install two 20 amp circuits and sump pumps with alarms for vault 1. Furnish and install 2 (two) condensate pumps on the exiting condensate tank located in the vault at the south west corner of building 010.(vault #2). Furnish and install two sump pumps with alarms within vault# 2. Furnish and install 2 new condensate pumps on the existing condensate tank located in room B2B4 of building 010. Make all electrical connections as necessary.
All electric located within the vaults shall be enclosed in water proof fixtures.
In accordance with this contract the contractor shall provide all labor, material, equipment and transportation to include all accessories and incidentals necessary to complete the job to government requirements. The facility under this contract may contain asbestos materials. The contractor is warned not to disturb any asbestos material during the performance of this work. Should the contractor encounter any material that in their judgement may contain asbestos, they must stop work immediately and notify the contracting officer (CO) within 24 hours.